Navionics Research Inc. is pleased to introduce a MODBUS/TCP and MODBUS/UDP CLIENT feature for its SCADA Server Software system!
Has your Water Utility ever had the need to monitor Office Infrastructure, such as Power, Generator Status, Physical Security (Entry & Motion Detection), Office Temperatures, Utility Consumption (Water, Gas, Electricity Meters), and Water Salesmen. If so, then this new software feature is made for you!
Most often, the SCADA Server is staged at the Water District Office, and the RTU equipment is installed at remote pumping stations, water towers, metering stations, valve stations, etc..
In order to monitor devices at the District Office, an extra RTU could be added to the system. However, Navionics Research recently developed and introduced an Economical Software Feature that leverages the existing Server computer to co-function as a local MODBUS-over-Ethernet client — thereby obviating the need for an additional RTU and its associated expense.
In a recent project, a client desired to monitor and alarm the Status of a Natural-Gas-Powered Backup Generator and Automatic Transfer Switch at the Water District Office using its SCADA system. The Water District office has two LANs (Local Area Networks) — one business network and one control network. A MODBUS I/O device was installed within the Automatic Transfer Switch enclosure and connected to the control network LAN.
The following I/O points were desired to be monitored, alarmed, and historically trended:
- Office Electric Load Transferred and Running on Generator Power (YES/NO)
- Generator Battery Voltage (Vdc)
- Generator Accumulated Runtime (Minutes)
The new SCADA software was configured to regularly poll the status of the MODBUS I/O slave using the MODBUS/UDP protocol over the Control LAN.
MODBUS I/O Device. In this application, a SCADAmetrics EtherMeter® was utilized as the Modbus slave device. The EtherMeter is a versatile Modbus/TCP/UDP device that features 3 digital inputs, 2 analog inputs, 1 battery voltage input, and 2 flow meter inputs.
ABOUT MODBUS: One of the key industrial protocols utilized within Navionics Research SCADA Systems, MODBUS has become a de facto standard of industrial communication protocols. It is an especially important protocol when connecting control equipment from an in-homogeneous set of manufacturers. Gathering momentum and support since 1979 when it was first introduced by Modicon (now a division of Schneider Electric), it is the most common means of connecting industrial electronic devices. It is openly published, royalty-free, and forms a relatively easy-to-deploy industrial network.
The new SCADA Server Software with MODBUS/TCP and MODBUS/UDP client drivers is now ready for general deployment. It is anticipated that its main usefulness will be in Office Facility Monitoring, such as Power, Generators, Physical Security (Entry & Motion Detection), Office Temperature, Utility Consumption (Water, Gas, Electricity Meters), and Water Salesmen. If you feel that this upgrade will be of value and benefit to you and the Water District, let me know and we’ll get started.
And as always, if you have any questions, please don’t hesitate to reach out by phone or email.
Telemetry, SCADA, & Controls Newsletter
Was this article helpful? Would you be interested in receiving updates such as these in our occasional email-delivered newsletter? If so, here’s our sign-up page: